Vehicles must be capable of safely towing any generator they pull, based on the rated capacity of the vehicle and the weight of the generator.
The weight of the generator is a safety concern not only for towing the unit, but particularly for being able to safely and effectively STOP with it in tow.
Emergency Generator Hookup Procedures Determine which generator should be used:
240 Volt 3 Phase 100 AMP
480 Volt 3 Phase 200 AMP.
Before towing a generator to another location:
MAKE SURE TOW VEHICLE CAN SAFELY PULL & STOP THE GENERATOR
Press the “ON” button on interlock, red indicator light should come on
Go to control panel in station, select a pump and switch it to hand (start only one pump at a time). Check rotation of pump, if rotation is correct switch HOA switch to “AUTO”. Station should operate normally.